Was requested to attend a client server room that was struggling to maintain temperature. Found R410a split system was short on refrigerant. Traced leak to evaporator, informed client and recovered the refrigerant as per FGas regulation. We provided the client options to repair or replace. Client opted to replace with new current R32 system that has been installed commissioned and is in operation.